Catalog No. 300 - Hot Socket Gap Indicator
The new TESCO Hot Socket Gap Indicator is used to determine if a meter socket jaw has become worn-out and unsafe for continued use. The Gap Indicator determines unsafe holding force on meter socket jaws based on laboratory testing.Read More
The TESCO Hot Socket Gap Indicator (Catalog No. 300-2) is quick, easy-to-use and has a rugged, non-conductive insulated shell. The mechanical tool engages the jaws of a meter socket and will indicate a gap or significant loss of jaw pre-load. Total estimated time of testing four jaws is less than 30 seconds. Even minor gaps can result in electrical arcing, resulting with a more serious problem, failure, or electrical fire.
The TESCO Hot Socket Gap Indicator will work with all sockets, including meter socket jaws with designed-in gaps, and socket jaws which have fresh lubricant.
Note: If feasible, service should be disconnected. Regardless of whether the service has been disconnected or is live, personal protective equipment (PPE) should always be used while operating.
See frequently asked questions about the Hot Socket Gap Indicator.Read Less
- Easy-to-use design
- Determines unsafe holding-force on meter socket jaws based on laboratory testing
- Blade spring force was designed to effectively determine a minimum unsafe threshold
- Insulated plastic body (Rated 3000 V)
- Tin-plated spring steel blade used to withstand daily use, travel, and vibration
- No maintenance required
- Calibrated for 5 years or 1,000,000 sockets (whichever occurs first)